2021 Alder Point Drive Roseville, CA 95661
Warranty: Not on file. Warranty Search Link
Voltage Range: 197-253
Max Circuit Breaker: 45
Min Circuit Amps: 26.4
Fan Motor: FLA 1.50 H.P. 1/4
Compressor RLA 19.9 LRA 109
Max Working Pressure: Unknown
Factory Charge OZ. R-410A: 104
Factory Test Pressure PSIG: 240-450
Heating & Cooling Issue/Inspection
Customer complaint of no heat
Checked all safety devices
System would not start
Check diagnostic code and unit was blinking three which is a pressure switch stuck open
Cleared and tested pressure switch and unit fired up
Tested from thermostat and unit is working
Recommend replacing pressure switch due to possible future failure.
Recommending sign up for RSA maintenance program.
Also talk to homeowners about ductwork issues. Returns are way too small for size of unit and the 12in duct is collapsed.
Ecology Air Innovations
Wire exposure. Attention recommended ASAP
Capacitor 1 overworked: Replacement recommended: 1 year part warranty.
Capacitor 2 overworked: Replacement recommended: 1 year part warranty.
Hard start kit recommended: 1 year part warranty.
Chemical wash recommended
Bonney Plumbing Heating and Air
Gen. Maintenance/ Estimate
AC Tune up
Temp split: 20 degrees.
OEM Blower motor amps ( 7.36 / 8.1 ).
Blower capacitor 20uf +- 5% ( 18.76 ) lowest is 19**.
Blower motor hot to the touch.
No oil on blower motor. Tightened low volt wires on board.
Cleaned blower cabinet.
Inspected evaporator coil.
Flushed drain line.
RLA ( 13.29 / 19.9 ).
FLA ( .64 / 1.5 ).
LRA ( 119.4 / 109 ).
Dual run capacitor 45 + 5uf +- 5% ( 34.8 ) ( 4.66 ) lowest is 42.75 / 4.75***.
Contactor is good.
Some oil on condenser fan motor.
Cleaned inside / outside of system.
Condenser coil was super dirty.
Cleaned condenser coil.
Replaced 2 disposable filters.
Unit is operating at this time.
Single run capacitor
Dual run capacitor
Compressor savor kit